Working Principle of Format Heat Exchanger
The plate heat exchanger is composed of a group of corrugated metal plates with holes on the plates, through which two liquids for heat transfer pass. The sheet metal is mounted in a frame with a fixed plate and a movable compaction plate on the side and clamped with clamping bolts. A sealing gasket is mounted on the plate to seal the fluid passage and guide the fluid to flow alternately into the respective passages. Fluid flow, physical properties, pressure drop and temperature difference determine the number and size of plates. The corrugation of the plate not only improves the turbulence degree, but also forms many supporting points, which can withstand the pressure difference between the media. The metal plate and the movable compaction plate are suspended on the guide rod and positioned by the lower guide rod, while the end of the rod is fixed on the support rod, but if one or two liquids pass through the heat exchanger more than once, the interface should be opened on the fixed plate and the movable compaction plate. In most cases, the use of one-way, all pipelines are connected to the fixed pressure plate, check the removal of heat exchangers, do not have to remove the pipeline.
1High heat transfer efficiency
2Safety and reliability in use
3Small area and easy maintenance
4 Adjust to changing circumstances
5Less resistance loss
6Favorable for the Utilization of Low Temperature Heat Sources